The following impacts the accuracy of measurement:
This application-specific measuring inaccuracy is constant for an installed sensor after approx. 1 hour of operation and can be adjusted as needed in a higher system (e.g. controller).
Powering the sensor requires a transformer for safety extra low-voltage (SELV) with separate windings for 100 % duty. When sizing and protecting the transformer, comply with all local safety regulations. When sizing the transformer, consider the sensor’s power consumption. For correct wiring, see the related device data sheets. Observe all permissible line lengths.
Cable routing and cable selection Note that when routing cables, the longer the cable runs and the closer the cables, the greater the electrical interference. Use shielded cables in EMC-prone environments. Twisted pair cables are required for both secondary supply lines and signal lines.